4/28/2014 3:03:07 PM
4/18/2014 2:09:10 PM
There are no annotations on this page.
Document management portal powered by Laserfiche WebLink 9 © 1998-2015
All rights reserved.
Pages to print
Enter page numbers and/or page ranges separated by commas. For example, 1,3,5-12.
After downloading, print the document using a PDF reader (e.g. Adobe Reader).
View plain text
ORDINANCE NO. 98-133 <br /> ' AN ORDINANCE OF THE CITY COUNCIL OF THE CITY OF <br /> GRAPEVINE, TEXAS AMENDING THE GRAPEVINE CODE OF <br /> ORDINANCES BY AMENDING CHAPTER 7 BUILDINGS AND <br /> CONSTRUCTION, ARTICLE I, SECTION 7-3 UNIFORM <br /> BUILDING CODE, 1994 EDITION AMENDMENTS, RELATIVE <br /> TO FIRE RESISTIVE REQUIREMENTS FOR GROUP R, <br /> DIVISION I OCCUPANCIES AND FIRE EXTINGUISHING <br /> SYSTEMS FOR GROUP R, DIVISION 3, SINGLE FAMILY <br /> DWELLING UNITS, REPEALING CONFLICTING ORDINANCES; <br /> PROVIDING A SEVERABILITY CLAUSE; PROVIDING A <br /> PENALTY, NOT TO EXCEED TWO THOUSAND DOLLARS <br /> ($2,000.00) FOR EACH SEPARATE OFFENSE AND A <br /> SEPARATE OFFENSE SHALL BE DEEMED COMMITTED <br /> UPON EACH DAY DURING ON OR WHICH A VIOLATION <br /> OCCURS; DECLARING AN EMERGENCY AND PROVIDING AN <br /> EFFECTIVE DATE <br /> BE IT ORDAINED BY THE CITY COUNCIL OF THE CITY OF GRAPEVINE, TEXAS: <br /> Section 1. That Chapter 7, Article I, Section 7-3, Amendments, is hereby <br /> -�� amended by amending Section 310.2.2 Special Provisions, first paragraph, to read as <br /> follows: <br /> "Group R, Division 1 Occupancies more than two stories in height or <br /> having more than 3,000 square feet (279m2) of floor area above the first story <br /> shall be of not less than one-hour fire-resistive construction throughout except as <br /> provided in Section 601.5.2.2." <br /> Section 2. That Chapter 7, Article I, Section 7-3 Amendments, is hereby <br /> amended by amending Section 904.2.10 Fire Extinguishing Systems to read as follows: <br /> "Sec. 904.2.10 All Occupancies. Approved automatic extinguishing <br /> systems shall be installed in all stories of buildings three (3) or more stories in <br /> height, excluding buildings used solely as parking garages, and Group R, <br /> Division 3, Private Dwelling Units. <br /> Buildings required to be sprinklered per Section 904.2.10 shall have a <br /> hydraulically designed sprinkler system that meets all the requirements of the <br /> Uniform Building Code Section 403.2.1. Standpipes may be combines with the <br /> sprinkler system." <br />
The URL can be used to link to this page
Your browser does not support the video tag.